a:31:{s:21:"return_visit_required";s:2:"no";s:7:"contact";s:4:"1324";s:15:"date_of_service";s:10:"10/18/2015";s:10:"start_time";s:6:"23:00h";s:8:"end_time";s:6:"05:00h";s:11:"total_hours";s:3:"6.0";s:18:"service_technician";s:2:"49";s:19:"canopy_manufacturer";s:5:"N / A";s:8:"model_no";s:5:"N / A";s:9:"serial_no";s:5:"N / A";s:4:"fuel";a:2:{i:0;s:11:"Natural Gas";i:1;s:8:"Electric";}s:14:"cooking_volume";s:4:"High";s:21:"exhaust_system_report";a:13:{i:0;s:4:"Pass";i:1;s:4:"Pass";i:2;s:2:"NA";i:3;s:2:"NA";i:4;s:4:"Pass";i:5;s:4:"Pass";i:6;s:4:"Fail";i:7;s:4:"Pass";i:8;s:4:"Pass";i:9;s:4:"Pass";i:10;s:4:"Pass";i:11;s:4:"Pass";i:12;s:4:"Pass";}s:20:"ecologizer_uv_system";a:3:{i:0;s:2:"NA";i:1;s:2:"NA";i:2;s:2:"NA";}s:17:"cooking_equipment";a:2:{i:0;s:1:"0";i:1;s:1:"1";}s:11:"leaks_found";s:2:"no";s:25:"exhaust_fan_belt_replaced";s:2:"no";s:18:"hinge_kit_required";s:3:"yes";s:8:"comments";s:45:"*** Next service due or before 04/17/2016 ***";s:13:"service_cycle";s:5:"6 mo.";s:11:"recommended";s:5:"4 mo.";s:10:"duct_width";s:0:"";s:8:"fan_base";s:0:"";s:15:"fan_base_height";s:0:"";s:16:"edge_base_height";s:0:"";s:14:"height_of_duct";s:0:"";s:9:"belt_size";s:0:"";s:13:"leak_location";s:0:"";s:5:"notes";s:1107:"- All exhaust fans require new hinge kits.  The existing are faulty or non-existent.

- 1 exhaust fan is in poor condition and not exhausting to full potential (CFM is lower than rated).  
Recommend replacing unit.

- Roof heavily soiled with grease.  

- Duct heavily soiled.  A 2nd visit is required to get these cleaned to BC Fire Code. 

- It is this technicians personal opinion that the previous service company did not clean or service the fans. 
The ducting has grease build up to a level that would indicate the last service was more than a year ago.

- Emergency lights have no service tag.  Unknown the last time the units have been tested for their annual 
inspection under the BC Fire Code.

- Could not locate Fire Suppression Cylinders, Unknown if they have been tested within 6 mo.

- leak found above the fish fryer.  Located above the canopy on the 2nd 45 Degree angle bend.  Weld Seam has hole in it.

- Note: Employees are unaware of fire safety procedures or how to use equipment should a fire occur.  
Recommend a fire training plan, we could assist with this.   
";s:22:"owner_authorized_agent";s:4:"1414";s:9:"locations";a:0:{}}